This control unit is used for connection into the WIS access system. Its construction makes it designated for installation into the lower ceiling with an ability to connect two reading units. It supports the WIEGAND, I2C or RS 232 interfaces of the connected reading units. It is equipped with a controlling microprocessor x51 and two subordinate processors which ensure communication with external reader heads. When it comes to operation, it can work in an online mode, with the ability to switch offline in case communication problems appear.
Versions of WBox_Rn control unit
|WIST0213||Control unit WBox_Rn||Plastic cover
|Dimensions||190 mm x 140 mm x 70 mm|
|Voltage/Power supply||9-14V DC|
|Max. consumption||150 mA pri 13V8
|Data memory||SRAM 128 kB backed up by internal battery|
|Galvanic separation||Only bus RS 485|
|Communication interface||RS 485 / RS 232|
|Number of all or nothing relays||2|
|Type of contacts||Choice between NO or NC|
|Max. switched current||6 A DC
|Number of reading heads||1 or 2|
|Interface of connected reading heads||I2C, WIEGAND, RS 232|
|Range of working temperatures||-25, +50ºC|
|IP coverage||IP 56 - plastic cover
The control unit contains predefined inputs and outputs. Their function is apparent from the connector description J4. The active state of the inputs is given by the configuration of the control unit, and configuration can only be done from the configuration utility.
While using the outputs (relay contacts) and controlling the charge of an inductive character the contacts must be connected correctly to the control unit. The positive pole of the controlled charge always must be connected to the NO or NC contacts. While controlling the electromagnetic locks the safety diode must be connected in reverse direction.